In the Lancaster area, Integrity Air Conditioning is well known for providing exceptional ac repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with Integrity Air Conditioning because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC Heat Pump & Furnace Repair in Lancaster, TX. Call us today at (972) 270-1244!
Fixed wiring unit is heating
Residential no cool
Found condenser fan motor seized up on air conditioning, replaced condenser fan motor and preformed a cooling maintenance on the system.
Replaced warranty condensor fan motor
Arrived at air conditioning service call. System not cooling. Found evaporator blower motor has failed. Replaced evaporator blower motor. System is cooling at this time
Arrived at air conditioning service call. Downstairs system is not cooling. Found a bad capacitor, replaced capacitor. System is operating properly at this time.
Installed indoor blower motor
Checked over system
Adder r22 refrigerant to old Trane system
Service completed by John.
Client wanted quote on duct cleaning and dryer vent cleaning I also talked about filtration with client
Found loose belt on air handler for package unit tightened belt
Maintenance and cleaned condensation line
Preformed maintenance on 4 ton carrier slot system also left client with estimates to make repair or replace