In the Plano area, Integrity Air Conditioning is well known for providing exceptional ac repair, installation, and service. The people we send out to serve you are also top notch, something you'll see in their reviews below. Everyone you deal with at our company has the goal of making sure your experience with us will be so good you'll call us every time you need help. You can feel confident working with Integrity Air Conditioning because we stand behind our work and comply with all local codes. This is why, as you can see by the map and reviews below, we are rated so highly for AC Heat Pump & Furnace Repair in Plano, TX. Call us today at (972) 270-1244!
Preformed a 6month install check unit is cooling
Follow up call on services by Daniel Sanders requested on 8/12 .
Found grounded compressor unplugged unit is running off one compressor for now will need to replace compressor
Cleared drain line
Follow up call on services by Cj requested on 7/6 .
Replacing of old Goodman 2 ton system , replaced Goodman with a Trane complete package
Added new 6” vent pipe to some machinery in warehouse job looks great client is pleased with work
Came to fix vent pipe had to reschedule due to electricians using lift
Routine air conditioning system
Residential ac maintenance
Duct work estimate
Commercial package no cool
Checked Freon levels
Changed condensor fan motor on one unit and preformed maintence on both units they both were low on refrigerant one will need to be replaced gave client options will return monday and put 410@ refrigerant in the carrier unit
Unit is leaking refrigerant located leak documented leak and gave client options
Residential air conditioning refrigerant leak
Commercial air conditioning repair
Residential air conditioning maintenance
Checked carrier split system unit was low on refrigerant blew the drain and made preventative suggestions to client they declined for now but did become member and will reach back out to us when ready to make further repairs unit is cooling just not 100%
Roof top package unit Trane system was low on r410 a refrigerant also added some uv stop leak need to return and replace shiv on motor and do maintenance on units
Heat not coming on! Thermostat issue
Maintenance heating and cooling checks also changed filters and waged condenser coils